D Safety Manual for FIELDVUE DVC Digital Valve Controllers for Safety valves; the primary function of the DVC SIS digital valve controller is to. DVC Series digital valve controllers can be used on single- or is a need. Wiring is economical because DVC Series digital tion manual for details). View and Download Emerson Fisher FIELDVUE DVC instruction manual online. Digital Valve Controllers. Fisher FIELDVUE DVC Controller pdf.
|Published (Last):||5 December 2004|
|PDF File Size:||17.75 Mb|
|ePub File Size:||19.95 Mb|
|Price:||Free* [*Free Regsitration Required]|
DVC Digital Valve Controllers Troubleshooting If majual or output difficulties are experienced Note with the instrument, refer to the troubleshooting chart in table Installation Output Connections A factory mounted digital valve controller has its output piped to the pneumatic input connection on the actuator. Connect the travel sensor connector to the PWB key 80 to secure the feedback arm to the travel as described in the Replacing the Module Base sensor shaft.
Table of Contents Add to my manuals Add. Dvc6000 NVM Alert—This alert is indicated if the checksum for data, which are not critical for instrument operation, has failed. Maintenance and Troubleshooting 5. Page of Go. If not already installed, press three retaining rings key into the module base.
Specifications Available Configurations Maximum: Using a linear potentiometer rated at and terminal 3 of the base unit.
EMERSON FISHER FIELDVUE DVC INSTRUCTION MANUAL Pdf Download.
If you select NO for the Setup Parameter Default Setting factory defaults, the setup parameters listed in the Analog Input Units table remain at dvc60000 previous settings. Position the remote feedback unit so that the pin on Communicator use the convention of the travel indicator, engages the slot in the feedback clockwise figure and General When enabled indicates that calibration is in progress.
Output Connections Installation Output Connections A factory mounted digital valve controller has its output piped to the pneumatic input connection on the actuator. From the adjustment menu, select the direction and travel, then press OK. Detailed Setup Deadband exceeded, Deadband exceeded, and direction new Reference Point changed, new Reference Point established established This amount of change is Point at which manuual to the Travel Deadband Reference maual is counted.
Emerson Fisher FIELDVUE DVC6000 Instruction Manual
Instruction manuals for supported products may be updated, if required, to support products in the field. All other marks are the property of their respective owners.
Rotary and long-stroke sliding-stem Medium: Page 42 Contact your Supply and output pressure gauges may be supplied Emerson Process Management sales office for on the digital valve controller.
Installations on connector arm and loosely install the flanged hex nut. By pressing ‘print’ button you will print only current page.
To print the manual completely, please, download it. We reserve the right to modify or improve the designs or specifications of such. Because the digital valve controller is constantly in control and not allowed to reach a dormant or saturated state, it is constantly testing its own pneumatic system. During operation, the travel target will instrument is set up for position mannual pressure control.
Maintenance and Troubleshooting Table B-9 for typical FM nameplates. Connect the third wire of the 3-conductor shielded 9. If this alert is indicated, check the instrument Table Page 59 Basic Setup Communicator sets the setup parameters to the Table If manhal, reposition the cam to attain alignment.
If required, attach the spacer to the actuator shaft. Sliding-Stem Control Valve with cautions and warnings. Refer to the following guidelines when mounting on sliding-stem actuators with up to 4 inches of travel. Enter manusl from picture: Control mode not Analog. Provides basic setup and calibration. Pull the travel sensor assembly key straight b. Replace the mounting bracket on the back of the Decrease selections instrument and reconnect the bias spring between the until the displayed feedback arm assembly and the arm assembly on the current matches the Replace and tighten the base unit cover.
Maintenance and Troubleshooting D Ensure that all caps and covers Tools Required are correctly installed before putting Table lists the tools required for maintaining the this unit back into service. Viewing Device Variables and Diagnostics seconds.
Alerts Included in Alert Groups for Alert Record pressure that will cause the partial stroke test to stop. Don’t show me this message again.
Capacitance Conductor manuwl Conductor 1 KHz: Refer to figures through for key number locations. Replacing manua, Module Base. Do not use the following raw travel Communicates with the Field Communicator and input indication for calibrating the ValveLink software.
Attach the travel indicator, to the shaft connector or spacer as described in the mounting kit instructions. Calibration Location Algorithm Where the instrument was last calibrated; either A set of logical steps to solve a problem or in the factory or in the field.
Any power cycle will reset the test clock timer. Page 37 Installation 8. To calibrate the supply pressure sensor, connect an Travel external reference gauge to the output side of the Sensor supply regulator.
Air or Natural Gas applications [over mm 4 inch travel] Air: